The C-TEC BF562-5 is a 24V 5A switch mode power supply which can accommodate up to 2 x 12v 18Ah batteries.
C-TEC’s next generation 5 Series
12V and 24V digital hybrid
switch-mode power supplies are
among the most powerful and
versatile on the market.
Third-party certified to EN54-4/A2
by the LPCB and VdS, they are ideal
for powering beam detectors, autodial communicators, aspirating
smoke detectors, auto-open vent systems, auxiliary
sounder systems or any other device performing a
mandatory function of a fire alarm system.
All models feature a plastic protective cover on their
internal PCBs to guard against live parts offering
full compliance with EN62368-1 (Information and
Communication Technology Equipment - Safety
With additional features such as deep discharge battery
protection, a single pole volt-free changeover relay,
a multi-function fault status LED, battery impedance
monitoring, dipswitch-selectable battery charging and
more, it’s no wonder they’re fast becoming the power
supplies of choice for installers across the globe.
Ideal for powering beam detectors, auto-dial communicators, aspirating smoke detectors, auto-open vent systems, auxiliary sounder systems or any other device performing a mandatory function of a fire alarm system.
The BF562-5 can be customised to suit your exact requirements using a BF423 configurator & PC. Configurable parameters include float voltage temperature compensation, battery charge rate (mA), battery impedance and configurable Input/Output settings. *It is important to note changing the PSU's parameters in this way is outside the scope of EN54-4 and any changes must be tested by the responsible person for correct operation.
PSU STATUS LED (located on the PSU PCB)
1 flash = Mains Failure.
2 flashes = Battery Voltage Low.
3 flashes = Battery Voltage Critical.
4 flashes = Charger Failure.
5 flashes = Charger OK (Battery is either actively charging, or in float charge).
6 flashes = No Batteries Fitted (indicating DIP Switch 4 position).
7 flashes = Battery Resistance Fault (Level set by DIP Switch 2 position).
8 flashes = Output Over Voltage.
BATTERY FAULT MONITORING
The BF562-5 complies with EN54-4/A2 and therefore must monitor battery resistance. The fault threshold is directly related to the ability of the battery to deliver the rated current to the load. For example, batteries stored uncharged for long periods, during shipment and/or distribution, degrade leading to increased internal resistance. If a degraded battery is fitted, a fault will be shown by the PSU as mandated by EN54-4/A2.
Data on the BF562-5's status can be extracted from the PSU's bi-directional data port. The data available includes thermistor measurements; battery terminal voltage; system voltage at load terminals; battery charge current; load current; battery impedance and ASCII text string status messages. Extracting this data requires additional equipment and permissions - contact C-TEC for details.